ULC is pleased to announce the publication of the Fifth Edition of CAN/ULC- S, Standard for. Inspection and Testing of Fire Alarm Systems. This National. Fire Alarm Inspection, Maintenance, and Service by Anubis Systems Technologies. SCOPE. This Standard provides requirements for the inspection and testing of fire alarm systems and specifies the devices and functions to be inspected.
|Published (Last):||24 February 2016|
|PDF File Size:||4.41 Mb|
|ePub File Size:||13.77 Mb|
|Price:||Free* [*Free Regsitration Required]|
Communication control enclosure bonded to ground. Obstructive material discharged during water flow tests?
CAN/ULC-S Fire Alarm Annual Inspection Test Form
Swing out Racks – lubricate and ensure proper operation. The tests reported on this form do not include the actual operational test of ancillary devices except where noted.
Never paint the sensor! Recommended Additional Testing not mandated by the Standard: Fifth year inspection items.
F Annual Tests Battery surface clean and dry? Diesel Natural Gas Other: Cap gaskets in place and in good condition?
Standards Council of Canada
Hand wheel is not broken or missing? Correct designations for common control functions and indicators.
Yes No NA Belt checked for proper tension? Plugging found in piping dismantled during alterations? Main drain test shall be s5336 on each system riser.
RPM Packing gland adjusted as required? Oil level in normal check sight glass Wet pit suction screens are unobstructed and properly installed Condition of oil in sight glass? Latches functional including break-glass type? If the sensor is part of an actual fire alarm system, make sure you alert other tenants in the building as to what you’re doing as well as your monitoring station if applicable.
S563 Rack Pressure Reducing Valves: Fire Alarm System Inspection Services.
Audible trouble signal operates. No Summary Work Order Number: AH R Record the battery terminal voltage after tests are completed. Circuits for emergency telephone trouble operation, including visual N indication, operates. Check concentration of antifreeze? Reconnect ancillary functions off site connections?
A specific reference to the Standard on the front page of the report i. Low water supervisory device inspected and tested.
CAN/ULC-S536-04 Fire Alarm Annual Inspection Test Form
J Upon failure of one amplifier, system automatically transfers to backup K amplifier s. Building Life Safety Audits.
Direct Connection yes no Number of Conventional Zones: Older model alarms may be switching normal household voltage VAC in order to sound an audible alert when a sprinkler head activates. E Tested and confirmed operation of supervisory relay. Low points in dry systems drained prior to freezing weather? Valve handles ucl place? Ancillary devices, which are powered from the control unit or transponder, are recorded.
All addressable devices must be individually listed on the Device Test Record sheet. Automatic transfer from alert signal to alarm signal operates.
Fire Alarm System Periodic Inspection (CAN/ULC-S)
Backflow prevention assemblies shall be inspected locked or properly supervised by an acceptable electrical means. Alarm device, test on dry pipe, pre-action or deluge system using bypass? Clean Cloudy Dirty Inspect duct work for combustion air? Will racks swing out of the cabinet at least ninety 90 degrees? Audibility of alarm sounder checked? I Terminals clamped tightly. Visual indicator test lamp test operates.
The applicable reports indicated below are attached hereto and comprise pages. In this instance the detectors are powered by a stand-by battery that will ensure continued protection even in the complete absence of electrical power or a “brown-out”. Have someone standing by the panel so that they can cancel or silence any audible alarm quickly.